Circadian lighting design
- 53 Visual lighting design
- 54 Circadian lighting design
- 55 Electric light glare control
- 56 Solar glare control
- 57 Low-glare workstation design
- 58 Color quality
- 59 Surface design
- 60 Automated shading and dimming controls
- 61 Right to light
- 62 Daylight modeling
- 63 Daylighting fenestration
- P2 Light at night
- P3 Circadian emulation
Circadian lighting design
To support circadian health by setting a minimum threshold for daytime light intensity.
Yes, for standing or adjustable desks, the vertical plane of measurement would be .46 m [18 inches] above the work surface, for example 1.58 m [62 inches] above the finished floor if a standing desk is fixed at 1.12 m [44 inches].
The owner must provide a compliant lighting system throughout the entire building, including all tenant spaces. Access to tenant spaces is required to conduct testing during Performance Verification, however, lighting provided by the tenant (if any) within their leased space is excluded.
Projects must consistently apply definitions to their spaces across all features. Thus, if conference tables, breakout tables or standing desks are also are characterized as "workstations" to comply with Feature 73 (and/or Feature 71), they are also considered workstations for the purposes of Feature 54.
Part 1a allows calculations and measurements to use daylight, which can be beneficial to projects with many windows. Part 1b only uses electric light, so outside conditions will not influence the performance results when tested. The WELL Performance Testing Agent will test for both pathways while on site to determine if the project passes either requirement.
Yes, computer screens can be included in calculations. Project teams are responsible for ensuring computer screens are turned on during Performance Verification.
A lighting designer is not required to be a part of the project design team; however, they may be helpful if no one on the project team has specific experience with lighting models or with circadian lighting design.
Yes, the project team is required to undertake light models or light calculations for this feature, as described in the feature language. However, the project team is not required to provide EML calculations or modeling for review; the only documentation required for this feature is a Letter of Assurance from the architect or lighting consultant.
The WELL Performance Testing Agent will verify that the levels are being met through on-site measurement of the light levels.
To learn more about circadian lighting and how it is measured, please review the Circadian Lighting Tables L1 and L2.
The circadian lighting levels created by the lighting system are dependent on the spectral power distribution of the light source used. Light sources with a higher melanopic ratio will produce more EML at a given brightness. As a rule of thumb, high correlated color temperature lamps and light fixtures tend to have higher melanopic ratios, but in the lighting model, project teams should calculate the melanopic ratio for the specific lights selected for use.
In order to fully verify the lighting strategy, a lighting model that takes into account all relevant light sources should be conducted to ensure that the required light levels are met at all the workstations on the vertical plane where the occupant's eyes would typically be.